The unit consists of two separate heat exchangers, which switches between operation and defrosting, to ensure continuous evaporation.
The heat exchangers are mounted onto a rigid frame with piping, valves, instruments, and a control panel for the automatic operation of the unit.
You obtain continuous evaporation by our set-up with 2 separate heat exchangers:
The heat exchangers are made in two versions depending on the environment. Either the CU version with aluminum finned cobber coils mounted in a powder-coated casing or a SS version with stainless steel coils and a galvanized steel casing for more aggressive climate conditions. Both versions come with a galvanized frame.
Equipped with low noise fans specifically designed to maintain uniform low-velocity airflow to ensure that water formed during defrosting is retained within the casing and led to drainage. A timer unit opens the solenoid valves alternately so that one unit is open to CO2 while the other is closed. When the tube bank is closed, the ambient air drawn through the unit defrosts the water ice formed during the “open tube bank“ cycle. The water collected in the aluminum drip tray during the defrost cycle is led to drainage. The evaporator is designed for installation inside a building.
|Looking for operating instructions, installation manual, spare part list etc.?|
|Please, send us your request|
As part of its separation into a new pure play water company, a new Pentair website has launched. Please visit the new Pentair.com to learn more about our exciting new company and your favorite brands!